Sample sizing calculations for BFW pumps and Fans for a typical Coal fired Boiler generating steam of 50,000 Kg/hr at 67 kg/cm2 and 485 degC. (110,000 lb/hr at 950 PSI & 905 F). Feed Water inlet at 105 C and Exhaust gas temp at 150 C.

Let us first calculate heat load and fuel consumption of the above boiler.

Pressure and temp at 1. Superheater Outlet : 67 Kg/cm2 & 485 C

2. Steam Drum : 73 Kg/cm2 & Saturated

3. Economizer inlet : Water inlet at 105 C

From Steam tables,

Enthalpy of Superheated steam , Hsh = 809 Kcal/ kg = 1456 BTU/lb

Enthalpy of Drum water , Hdwat = 305 Kcal/kg = 549 BTU/lb

Enthalpy of inlet water , Hwat = 105 Kcal/kg = 189 BTU/lb

Assume 3% Blowdown from Boiler.

Total Heat Load of the Boiler = Total heat absorbed by water to convert to steam + heat absorbed to get superheated + Blow down losses

= 50000(809-305) + 50000 x 1.03 x (305-105)

= 35.5e06 Kcal/hr = 140.87e06 BTU/hr

Fuel consumption = Heat Load/ (HHV x Efficiency)

= 35.5e06/ (7278 x 0.8649)

= 5639 Kg/hr = 12428 Lb/hr of coal

From previous article on Combustion and efficiency,

Wet gases = 14.05 and Air = 13.12 kg / kg of coal

Therefore, Exhaust gases produced = Fuel consumption x UnitWetGas

= 5639 x 14.05

= 79,228 Kg/hr of wet gases

Combustion Air required = 5639 x 13.12

= 73,984 Kg/hr of combustion air

Feed Water required = 50,000 x 1.03 : 3% Blowdown

= 51,00 Kg/hr

Sizing Calculations :

a) Boiler feed Water Pumps :

Two pumps of 100 % capacity are required one for working and one for standby.

Each pump discharge capacity minimum= 51500 Kg/hr

= 51500/950 : 950 kg/m3 water density

= 53.8 m3/hr

Margin on discharge capacity : 15- 25 %.

Take 20% margin in this case.

So discharge capacity of each pump : 53.8 x 1.2

= 64.6 m3/hr =say 65 m3/hr

If Recirculation valves are not provided, you need to add min recirculation flow to the above figure, which may be about 6-10 m3/hr depending up on pump type and make.

Pump head required = Drum Pressure + Drum elevation + Piping Losses + Control Valve Loss + Other valve losses

= 75 Kg/cm2 + 2.0 + 2.0 +5.0 +2.0

= 86 Kg/cm2

= 86 x 10/0.95 mts of water head at 105C

= 905 mts of WC

Provide up to 5% margin on head. So final Pump head is 905 x 1.05 = 950 m of WC

So BFW pumps (2 nos) rating is 65 m3/hr at 950 m of WC with feed water at 105 C.

b) Sizing calculations of FD Fan :

Forced Draft Fan is required to pump in primary combustion Air into the Boiler furnace. Air from FD fan passes through Air Heater before entering furnace through Grate. Secondary Air Fan (SA fan) supplies secondary combustion air in to the furnace. Usually primary air is 70 -80 % of the total air and balance is supplied as secondary air through SA fan. Secondary air is supplied at a higher pressure to help fuel spreading on the grate called as pneumatic spreading.

Total combustion Air, Kg/hr = 73,984

= 73994/(1.17 x 3600) m3/s :Air density-1.17kg/m3

= 17.56 m3/s

Primary Air , 70% of total , m3/s = 0.7 x 17.56

= 12.3 m3/s

Take 20% margin on discharge capacity. So FD Fan flow is 1.2 x 12.3 = 14.76 m3/s

Head required = Draft loss across Air Heater + Grate + Ducting & others

= 75 mmWC + 75 + 50 mm : Approximate

= 200 mm WC (approximate)

Take 15-20 % margin on head. So FD fan head should be about 230 mm of WC.

Therefore, FD fan rating is 15 m3/s of air at 230 mm WC static head.

Power requirements of FD Fan :

Let us assume Fan efficiency as 75% and Motor Efficiency as 90%.

Power required for FD Fan, BHP = Flow x Head / ( Efficiency x 75.8 )

= 15 x 230 / ( 0.75 x 75.8 )

= 60.7 HP

Motor HP required = 60.7 / 0.9 = 68 HP

Annual cost of operation assuming 7 cents per KWH and 7200 hrs of operation per annum. 0.74 is factor for converting HP to KW. Pl note that unit Electricity charges vary widely across different countries.

= 68 x 0.74 x 0.07 x 7200

= $ 25, 362 /-

c) Sizing calculations of SA Fan :

Secondary Air Fan (SA fan) supplies secondary combustion air in to the furnace.

Secondary Air , 30% of total , m3/s = 0.3 x 17.56

= 5.27 m3/s

Take 20% margin on discharge capacity. So SA Fan flow is 1.2 x 5.27 = 6.3 m3/s

SA fan static head is about 630 mm WC.

Therefore, SA fan rating is 6.3 m3/s of air at 650 mm WC static head.

Power requirements of SA Fan :

Let us assume Fan efficiency as 70% and Motor Efficiency as 90%.

Power required for FD Fan, BHP = Flow x Head / ( Efficiency x 75.8 )

= 6.3 x 650 / ( 0.7 x 75.8 )

= 77.1 HP

Motor HP required = 77.1 / 0.9 = 86 HP

Annual cost of operation assuming 7 cents per KWH and 7200 hrs of operation per annum. 0.74 is factor for converting HP to KW. Pl note that unit Electricity charges vary widely across different countries.

= 86 x 0.74 x 0.07 x 7200

= $ 32,075 /-

d) Sizing calculations of ID Fan :

Induced draft fan or ID Fan is required to evacuate the exhaust gases from Boiler to atmosphere through Duct collectors and chimney. Usually ID should take care of draft loss across the Boiler from furnace to Air heater and then draft loss across Duct Collectors like ESP, Wet Scrubber or mechanical type Cyclone dust collectors .etc.

Total wet gases, Kg/hr = 79,228

Gas Density = 1.3265 Kg/Nm3

Therefore, gas flow in Nm3/hr = 79,228 / 1.3265

= 59227 Nm3/hr

= 16.6 Nm3/s

Gas flow at 150C in m3/s = 16.6 x (273+150)/273 = 25.7

ID Fan capacity taking 20% margin on flow = 25.7 x 1.2

= 30 m3/s

ID Fan static Head = Draft Loss in (Boiler + Duct + Dust collector)

= 150 + 50 + 50 mm WC : Approximate

= 250 mmWC

Taking 20% margin on head, ID Fan head = 250 * 1.2 = 300 mm WC

Power requirements of ID Fan :

Let us assume Fan efficiency as 75% and Motor Efficiency as 90%.

Power required for ID Fan, BHP = Flow x Head / ( Efficiency x 75.8 )

= 30 x 300 / ( 0.75 x 75.8 )

= 158 HP

Motor HP required = 158 / 0.9 = 175 HP

Annual cost of operation assuming 7 cents per KWH and 7200 hrs of operation per annum. 0.74 is factor for converting HP to KW. Pl note that unit Electricity charges vary widely across different countries.

= 175 x 0.74 x 0.07 x 7200 = $ 65,268 /-

bagaimana mendapat training boiler dari perusahaan boiler tersebut

ini om marbun dari atmindo kah ?

Calculation-nya mungkin perlu di review lagi yach…

Untuk menghitung kebutuhan Coal, dari perhitungan tersebut :

Fuel consump = Heat Load / (HHV x Eff)

Mungkin lebih tepatnya bukan HHV tapi harus digunakan LHV.

Kalau HHV khan Gross, nah kalau LHV sudah Nett, untuk heating value-nya.

Regards,

Novi

IT is a good guide. Can u provide me method for calculation of head losses in ducts from PA/SA fan to boiler?

Perhitungan spt itu sangat bagus buat kita. Bisa dijadikan sebagai Referensi buat Pendekar Boiler Engineer… Pak Yanuar Alamsyah.. semoga Boiler Medco ga masalah lagi,,

amin….

tapi saya sekarang sudah tidak di medco pak, sudah resign. pindah ke south pasific viscose, ngerjain boiler CFBC & AFBC

this is marvellous information thankyou alam please arrange more detail calculation of boiler efficincy turbine efficiency boiler losses turbine losses

thanks arvind, i will than :)

Apakah mungkin bila boiler yang dibuat menggunakan burner dngan teknologi intermediasi yang saya kembangkan, karena burner ini dapat meningkatkan efisiensi energi dan hasilnya tidak berasap dan berbau

mungkin apa mas ?

Maaf pak alam, mungkin saya bertanya hal yg mendasar.. saya masi baru…

tp itu nilai HHV 7278 darimana y? sama efficiencynya 0.8649 jg, apakah itu memang spek yang di keluarkan oleh si pembuat boiler atau gimana.. soalnya saya cari artikel combustion and efficiency koq g ada y..

terima kasih pak..

very useful info

Thanks very much for your nice sharing..

I will very much from your sample calculation..

Bravo..

Regards,

M. Taufik

Go2Alam, Sama seperti Ariezky di atas saya juga tidak menemukan artikel mengenai efficiency dan combustion.. Saya sedang mau belajar mengenai bagaimana menghitung efisiensi penggunaan fuel pada boiler (batu bara dan gas)

Terima Kasih

I need feed pump capacity calculation & chimney height calculation

Tks pak, atas referensinya

i want some more information about boiler.i m a trainee engineer in bagasse based power plant.so plz help me.

Thns

In formula for power required by individual fans; there is a constant 75.8, with other variables. Can your please give some light over the constant?

can you help me to determine the ID Fan, BFW pump & FDF capacity for a biomass steam boiler which producing 45,000 kg/hr @ 30 barg & 350 C.

10 tph boiler feed pump capacity

R,sir

i appreciate your calculation on power plant which it giving star in calculation.now i need your help for calculation nd design of main steam line pipe dia slection as per boiler tph nd send me all calculation of power plant equipment nd aux.

Thanks

With regards.

S.n pandey

09780713103

Sir kindly send me all type of calculation in power plant

Hi webmaster do you need unlimited articles for your website ?

What if you could copy article from other sites, make it pass copyscape test and publish on your page – i

know the right tool for you, just type in google:

loimqua’s article tool